A brief description
This customers old filtration system was installed in the garage by a plumber.
The pump was fitted incorrectly as the pressure switch was on the bell housing and there was no expansion tank. The backwashing filter had the media topped up so the water remained acidic causing staining to sanitary ware in the bathroom and kitchen. A new backwashing pH corrector has being fitted with a new 20″ BB housing and a pro-3 with an auto shut off.
To stop the pump cycling on and off, a 100 litre expansion vessel was fitted to the system more efficient in the long run.
Posted by Kirsten Scott, 06.08.2021